Before operating, make sure that the level Ph of the water is 7.2 - 7.6 and chlorine levels are normal. For the first time, set the level knob on the controller to the maximum position, regardless of the volume of the pool and start the pump. Every day after the start check the level of copper using a copper test kit. When the copper level reaches 0.5 ppm, set the control knob to a level compatible the pool volume specified in the table on the controller. The values of the levels specified in the table are only approximate and match filter time 8 hours per day. If the filtration time 24 hours a day, the level value will be 1/3 of indicated in the table. The value of the level depends on the temperature and the pool load and may be different from those recommended in the table. The level should be set such that the copper concentration was 0.5 - 0.9 ppm. When the copper concentration reaches 0.5 ppm, the concentration of chlorine can be reduced by 70 - 80% and maintain about 0.1 - 0.2 ppm. Very convenient to maintain the concentration of of chlorine used automatic chlorine feeders. Ph maintain 7.2 - 7.4. Also can to add a polymer flocculant for possibility more crystal clear water. Once a week, check the condition of the electrodes, and if they are very small (less than 1 cm in diameter), they must be replaced with new ones. Typically, electrodes must be replaced after 10 months to 3 years (depending on the size of the pool and modes of operation).
Differences of operation for DS-200 differs only in the way to set the level on the controller, which is set after the copper concentration
reaches 0.5 ppm and calculated by the formula: L=V/t*0,3
V - the volume of pool (m3),
t - the time of pump operation during the day (hours)
This value of level is only approximate and is used only in the first time of operation. It may differ from the actual level values for to maintain the copper concentration of 0.5 -0.9 ppm during of operation. During operation adjust the level value so as to maintain the concentration of
copper in the range 0.5 - 0.9 ppm. All other so-same as guide for DS-50, DS-100.